# Performance Analysis of Dynamic Balance Electric Control Valve

Different from the traditional electric two-way valve, the dynamic balance electric control valve is an integrated product of dynamic balance and electric adjustment. The adjustment process is constant, that is, the valve authority is always 1, and its ideal characteristic curve can be realized, thereby achieving the ideal temperature control effect.

The relationship between the flow rate of the dynamic balance electric valve and the pressure difference on both sides of the valve at different opening degrees is shown in the figure below. It can be seen from the figure that in order to achieve the required flow rate, the minimum working pressure difference needs to be met. When the degree of pressure is constant, when the actual pressure difference between the two ends of the whole valve is less than the minimum working pressure difference, the flow increases with the increase of the pressure difference between the two valves. When the minimum working pressure difference of the valve is reached, the flow through the valve will remain constant. , no longer changes with the increase in the differential pressure across the valve. Only when the opening of the regulating spool changes, does the flow change.
From the formula, it can be obtained that the flow through the valve is related to the opening degree of the valve and the pressure difference behind the valve, and the control system outputs the corresponding signal to the valve according to the load change to adjust the opening degree of the valve, so as to achieve the corresponding flow. Therefore, as long as the pressure difference before and after the valve can be adjusted constantly, it can be ensured that the change of flow is completely determined by the valve opening, that is, it corresponds to the load change, and is not affected by the system pressure fluctuation caused by the influence of other valve switches, so as to achieve dynamic Balanced effect. The adjustment of any branch will not interfere with other branches, and any branch will not be affected by the adjustment of other branches.
In the air-conditioning water system, in order to achieve a good control effect, the characteristics of the best control valve should be equal percentage characteristics, also known as logarithmic characteristics, this curve is also called the ideal characteristic curve of the valve. If an air-conditioning system cannot maintain a good linear relationship between the opening of the control valve and the heat dissipation of the air conditioner, it will cause frequent temperature fluctuations and long system stabilization time.

## Share:

### Key points of water supply and drainage system valve selection

[ad_1] Today, I will talk to you about the key points of valve selection for water supply and drainage systems. The small valve allows you

### Standard Specification for Stainless Steel Ball Check Valves

[ad_1] Stainless steelStandard Specification for Ball Check Valves Stainless steel ball check valve is stainless steelMaterial ball check valve.Another name for ball check valve isinversestop

### The structure of stainless steel globe valve

[ad_1] Stainless steel globe valve is a kind of globe valve, English name:stop valve, Globe Valve. The stainless steel globe valve has relatively high requirements

### Analysis and Treatment of Butterfly Valve Closing Fault

[ad_1] 1 Overview of faulty butterfly valve Qinshan Hydropower Station adopts PDF130-WZ-280 butterfly valve, which is a horizontal double-plate valve structure.butterfly valveThe final assembly includes

### Cast Steel Check Valve-DIN

LUCKY6S is Chinese leading manufacturer and supplier of industrial valves. which has over ten years of experience in manufacturing high-quality industrial valves, focuses on delivering safety, efficiency, and cost-effectiveness to every industry that requires automation. We are committed to supplying premium industrial valves and equipment to distributors, importers, and project managers worldwide.